CONTACT WALL STATION NON-DIM SWITCH WITH OCCUPANCY SENSOR
1.) The Contact Wall Station Non-Dim Switch with Occupancy Sensor is a designer-style, multiple-detection technology, and universal voltage occupancy sensing wall switch.
2.) The Contact Wall Station Non-Dim Switch shall be designed to accept and control universal voltage (120VAC to 277VAC, 60Hz.) and rated to control up to 1000VA lighting loads.
3.) The Non-Dim Switch shall be a two-wire switch capable of handling the following loads:
a.) Incandescent / Quartz Halogen.
b.) General Inductive.
c.) Cold Cathode / Neon.
d.) Electronic Low-Voltage.
e.) Magnetic Low-Voltage.
f.) Fluorescent Non-Dimming Ballasts.
4.) The Non-Dims integral occupancy sensor shall have a viewing area of not less than one hundred seventy (170?) degrees at an axial distance of forty feet (40'), fifty feet (50') at 0 degrees, and shall have a total coverage area of not less than four-thousand square feet (4,000 Sq. Ft.) with an unobstructed view.
5.) The non-dim shall be supplied with color-coordinated, self-sticking masking labels that reduce the field of view of the occupancy sensor to 60, 90, or 120 degrees.
6.) The non-dims integral occupancy sensor shall utilize non-intrusive, passive detection technologies consisting of:
a.) Passive Infrared (PIR) to read and detect occupants' body heat and
b.) Enhanced PIR with Digital Signal Processing (DSP) to read and detect
occupancy throughout the entire space.
c.) Photo detection to sense human motion and help differentiate this signal
from other sources such as hot air vents.
7.) Under no circumstances shall the non-dims integral occupancy sensor emit energy of any type into the space that can potentially interfere with electrical, electronic, or medical devices (i.e. hearing aids).
8.) Each non-dim shall provide manual on/automatic off or automatic on/ automatic off operation and accept on/off commands from an unlimited number of multi-location 3-way Contact Wall Station Channel Remotes.
9.) Contact Wall Station Channel Remote stations shall provide multi-location On / Off control of the switch using conventional 3-way wiring.
10.) Each non-dim shall be capable of 4 time-out methods to adapt to the space:
a.) Manual fixed time (user definable) from 1 to 30 minutes.
b.) Auto Time Out Calibration - Conservative Mode.
c.) Auto Time Out Calibration - Normal Mode.
d.) Auto Time Out Calibration - Aggressive Mode. In Auto Time Out
Calibration Mode the non-dim shall automatically adapt the time out period
to the occupancy patterns of the space to maximize energy savings while
minimizing distraction to the user.
11.) The non-dim shall, when manually turned off by the user, continue to monitor the space, but will not turn on the lights. Once the non-dim detects a continuous vacancy for a period of five (5) minutes, the non-dim will rearm itself for automatic on (if so programmed). User shall be able to, at anytime, override this feature by manually turning on the lights.
12. Each non-dim shall, at the user's discretion, be programmed (at the sensor) to automatically adapt its programming parameters to optimally set time delay according to the space's occupancy/vacancy patterns.
13.) The non-dim shall, at the user's discretion, be programmed to prevent the automatic turning on of lights, when in automatic on mode, by either:
a.) Selecting one of eight (8) preset ambient light levels offered by the
b.) The sensor self-reads and permanently stores a specific ambient light
c.) This programming feature always allows for manual override "On" or "Off"
when more or less light is needed or desired by the user.
14.) The non-dim's operational/parameter programming shall be accomplished with the non-dim installed and operational without the need to remove the non-dim (or its faceplate) from its installed location.
15.) Each non-dim shall provide a LED indicator to provide indication when the sensor detects movement.
16.) The non-dim shall offer the selection of three user-programmable warning tones before automatically turning Off. The non-dim shall also offer the ability, to the user, to turn off warning tones.
17.) The non-dim shall mount in a single gang wallbox and be gangable with other designer-style electrical devices and faceplates.
18.) Each non-dim shall include a designer-style screwless, detachable color-coordinated faceplate in White, Ivory, or Light Almond.
19.) The non-dim shall be UL Listed to U.S. and Canadian standards for a 120VAC to 277VAC capacity.